Various defined protection methods can be utilised to mitigate the risks associated with the hazards of a hazardous area. These protection methods are engineered solutions to either remove one of the parameters required for an explosion or in the case of Ex d flameproof contain any explosion to prevent it propagating outside the protection containment.
All electrical equipment in the hazardous area must comply with EN 60079-0 the general standard, except were it is over ridden by one of the other standards specific to the protection method.
The primary electrical protection methods are:
|Ex d||Flameproof||EN 60079-0||Contain the Explosion|
|Ex e||Increased Safety||EN 60079-7||Non Sparking|
|Ex i||Intrinsic Safety||EN 60079-11||Power limitation|
|Ex t||Enclosure||EN 60079-31||Dust only|
|Ex n||Various1||EN 60079-6||non sparking|
|Ex p||Pressurised||EN 60079-2||see EN 61241-4 for Dust|
|Ex m||encapsulated||EN 60079-18||rarely used on its own|
|Ex o||Oil Filled||EN 60079-6||Rarely used|
|Ex q||Powder filled||EN 60079-05||Rarely used|
|Ex s||special||EN 60079-33||Used when no other method applies|